GI Combination Safety Shower & Eye Washer Standard: EN 15154-1:2006 & EN 15154-2:2006.
GI Combination Safety Shower & Eye Washer Combination of eyewash and a safety shower. The shower is activated by a pull rod and eyewash is activated by a flag handle or foot treadle. Two spray-type outlet heads deliver a flood of water for rinsing eyes. Connect unit to an uninterruptible water supply capable of delivering required flow when all components are operated simultaneously. Shower can provide 76 liters of water per minute. Center of the water pattern 16" from any obstructions. Large area covers of water flow, at 60", the water pattern covers 20" in diameter. Ball valve activates within one second. Easily located, accessible actuator no higher than 69". Eye washer unit deliver 11.5 liters of water per minute Shower Head: 8" diameter head provides water flow. Shower Valve: 1" IPS Stainless Steel ball valve. The valve is activated by a pull rod. Spray Head Assembly: Two spray heads. Each head has a dust cover, internal flow control, and filter to remove impurities from the water flow. Eye Wash Bowl: 11-1/2" diameter. Bowl is ABS plastic. Eye Wash Valve: 1/2" IPS Stainless Steel ball stay-open ball valve. The valve is activated by a flag handle or foot treadle. The unit remains in operation until the handle is returned to closed position. Pipe and Fittings: Schedule 1-1/4",1" and 1/2" galvanized steel. Furnished with yellow polyethylene covers for vertical piping for corrosion resistance. Supply: 1-1/4" NPT female inlet. Waste: 1-1/4" NPT female outlet. Working Pressure: 0.2-0.8Mpa flow pressure, 0.9Mpa maximum static pressure. Quality Assurance: Valve, bowl, and spray head assembly are factory assembled.